⬇️ Scroll down for virtual tour!
🗄️ Current server rack capacity
🗄️ 32 racks which are 75cm width, 107cm depth racks, 42U height
🗄️ 168 racks which are 60cm width, 120cm depth racks, 42U height
⚡ Power capacity
⚡ Currently installed 400V 1600kVA (1MegaWatt for servers + cooling!). Upgrade able to 10MW!
⚡ Backup generator
⚡ A and B 11kW 16A-3ph feed to each rack
⚡ Available power systems
⚡ 400V 3phase AC / 230V 1phase AC
⚡ 350V DC
⚡ 48V DC
♻️ Cooling and heat
♻️ 100% renewable power. (Hydroelectric)
♻️ Local reuse of waste heat to heat building. (similar as this video link)
♻️ Future planned remote supply of heat to district heating.
Room to grow
🌩️ Network capacity
🌩️ Redundant meet-me network rooms with inexpensive cross-connects.
🌩️ Racks are pre-cabled with at least 24 fibers to each meet-me room.
🌩️ Dark fiber providers on-net
🌩️ Network/metro providers on-site:
🌩️ Local peering fabrics on site
🌩️ Network latency (Round Trip Delay)
Oslo – London as low as 15ms (on north sea route)
Oslo – Copenhagen around 7ms
Oslo – Stockholm around 7ms
Oslo – Amsterdam as low as 19ms